Dose: Approximately 2 oz (60 ml) on systems up to 10 tons. 4 oz (120 ml) up to 20 tons.
- Use under 40 psi. If needed, perform a pump down by closing high side valve to reduce low side pressure.
- Connect male adapter to end of syringe, and purge air out of hose by pushing sealant through clear hose.
- Connect female adapter to low-pressure port side and push in with the syringe plunger.
- Allow 30 minutes for the seal to take place with system running.
*Cannot be used on high (liquid) side, only low side.